Website & Forum Discussions
Check here for our Welcome Message
Moderators: administrator, OutBack, OutBack Moderator Team
Okay-I jumped in with my Ccard and bought 20 Evergreen ES-E-200 fc3.
Pmp of 200w
Pmp max 204.99w
Pmp min 200w
The issue--The FMax 80 and the string Calculator tells me I can set up 3 strings of up to 24 panels. Using a Outback 3048.
While I am still considering a stand alone array, I could get 21 on my roof which faces perfectly South at a Pitch of 52 degrees and no shading. A Clear and cold location at 9200'.
What will happen if I integrate one different make Panel into my 20. For instance a Sun 7-KP-SE-200 which has:
Or what should I look for to minimize the Specs?
What happens if I add 4 Panels to make up the 24 max?
- Posts: 6
- Joined: Fri Feb 03, 2012 10:00 am
4 would mean 148 volts oc . With cold conditions that is too high,so I think you will need to stay with 3 in series .
1820 pv. fm80. 4times rolls 450 ah 24 volts. victron battery monitor. outback fxr 2000 watt inverter
- OutBack Guru
- Posts: 258
- Joined: Fri Aug 06, 2010 4:35 pm
- Location: NewZealand North Island
- My RE system: 1810 watt pv, fm80, outback vxr 2000 watt inverter. Rolls s600 times 4 24 volt system victron battery moniter.
petertearai wrote:4 would mean 148 volts oc . With cold conditions that is too high,so I think you will need to stay with 3 in series .
I agree with you guy.. Same answer from my side..
- Junior Member
- Posts: 1
- Joined: Sat Oct 20, 2012 12:47 am
- My RE system: no one
Return to Website & Forum
Users browsing this forum: Yahoo [Bot] and 1 guest